11/24/35KV Switchgear/Switch Cabinet/ Switchboard/ Electrical cubicle/KYN28A-12
|Min. Order:||5 Set/Sets|
|Delivery Time:||30 Days|
|Packaging:||Normal Export Wooden Case|
|Place of Origin:||Shanghai, China (Mainland)|
|Supply Ability:||1000 Set/Sets per Month|
Model No.: KYN28A-12
I. General Description
KYN28A-12 type metal-clad removable enclosed Switch Cabinet (called switch cabinet for short). It is applicable for power receiving and distribution in the 3.6-12Kv three-phase AC 50Hz single bus bar and single bus bar sectioning system. It has the functions of controlling, protecting and monitoring the circuit.
II. Operating Environment
a. The Ambient temperature upper limit and lower limit are respectively +40°C and -40°C; (allowing storage and transportation at -30°C);
b. Altitude is not more than 1000m;
c. Relative humidity: daily average value should not be more than 95%, while monthly average value should not be more than 90% (+25°C);
d. Seismic intensity should be not more than 8°;
e. Places without fire, explosion risk, serious pollution, chemical corrosion and violent vibration.
IV. Design & Structure
The switch cabinet is metal-clad. Its structure design accords with the standards GB3906-91, IEC298, DL404 and DL402. The crust structure is made of steel plates by means of bending and welding, which are joined by bolts. The hand buggy panel is the door of cabinet. The bosom of switch cabinet is divided into a breaker chamber, a main bus bar chamber, a cable chamber and a relay chamber by metal partitions. The degree of protection of the entire crust and compartments is IP2X equally. All the metal structures are connected to ground reliably. All the compartments of main circuit system have pressure release channels for independent exhaust.
V. Main technical parameters of switch cabinet VI. Ordering Instructions
The purchaser should supply following information for ordering.
a. Scheme of primary circuit
b. Types and specifications of electric components in the Switchgear;
c. Material quality and specifications of main bus bar and branch bus bar (according to the manufactory’s standards if not specified);
d. Schematic diagram of small wiring or standard schematic diagram, miniature bus bar array diagram and terminal diagram;
e. Coating color of switchgear;
f. Names and quantity of spare parts
g. Please negotiate with the manufacturer on special requirements. Contact us if you need more details on High Voltage Panels. We are ready to answer your questions on packaging, logistics, certification or any other aspects about Hv Switchboard、Power Plant Switchgear. If these products fail to match your need, please contact us and we would like to provide relevant information.